CITY OF LOS ANGELES CALIFORNIA
BUILDING AND SAFETY COMMISSIONERS
BUILDING AND SAFETY 201 NORTH FIGUEROA STREET LOS ANGELES, CA 90012
VAN AMBATIELOS PRESIDENT
RAYMOND S. CHAN, C.E., S.E. GENERAL MANAGER
E. FELICIA BRANNON VICE-PRESIDENT
ERIC GARCETTI MAYOR
JOSELYN GEAGA-ROSENTHAL GEORGE HOVAGUIMIAN JAVIER NUNEZ
FRANK BUSH EXECUTIVE OFFICER ____
Neogard A Division of the Jones-Blair Company 2728 Empire Central Dallas, Texas 75235 Attn: Rayhan Majid (214) 353-1600
RESEARCH REPORT: 25702 (CSI #07180) Expires: Date Issued: Code:
June 1, 2018 May 1, 2016 2014 LABC
Local Representative: Jim Nelson (775) 324-5524 GENERAL APPROVAL –Renewal - AUTO-GARD and AUTO-GARD FC Elastomeric FireRetardant Deck Coating System for Parking and Walking Decks. DETAILS AUTO-GARD Deck Coating System consisting of: 7780/7781 Primer, 70410 CA Base Coat, 7430 Series CA Wear Course & aggregate and 7430 Series CA Top Coat. AUTO-GARD FC Deck Coating System consisting of: 7780/7781 Primer, FC 7500/FC 7960 Base Coat, FC 7520/FC 7962 Wear Course & aggregate and FC 7520 /FC 7962 Top Coat. The roof system is approved for use as a fire-retardant deck coating as required by the Code. The approval is subject to the following: 1.
The deck coating components (except for the sand) shall be delivered to the jobsites in sealed containers identified by the manufacturer's name and product designation.
Application of the components shall be onto a concrete deck in accordance with the manufacturer's instructions (a copy shall be available at the jobsite) consistent with the description and requirements herein. All surfaces which are to be coated shall be free of water, curing compounds, bond breakers, hardeners, oil, etc.
RR 25702 Page 1 of 2 LADBS G-5 (Rev.08/08/2014)
AN EQUAL EMPLOYMENT OPPORTUNITY - AFFIRMATIVE ACTION EMPLOYER
Neogard Re: AUTO-GARD and AUTO-GARD FC Elastomeric Fire Retardant Deck Coating System for Parking and Walking Decks. DISCUSSION The report is in compliance with the 2014 Los Angeles City Building Code. The approval is based on tests in accordance with ICC ES AC 39. Addressee to whom this Research Report is issued is responsible for providing copies of it, complete with any attachments indicated, to architects, engineers and builders using items approved herein in design or construction which must be approved by Department of Building and Safety Engineers and Inspectors. This general approval of an equivalent alternate to the Code is only valid where an engineer and/or inspector of this Department has determined that all conditions of this approval have been met in the project in which it is to be used.
____________________________ QUAN NGHIEM, Chief Engineering Research Section 201 N. Figueroa St., Room 880 Los Angeles, CA 90012 Phone- 213-202-9812 Fax- 213-202-9943 DE RR25702/MSWord2007 R05/07/16 TLB1600105 1501/1504
RR 25702 Page 2 of 2